The following is an overview of the user manual for the Z-Wave product Nexello 3I/3O Hybrid Module (PLHA10100)from ABUS. To view other Z-Wave products and manuals from ABUS follow that link.
Three Inputs for the connection of:
Analogue sensors with voltage 0~12V
Digital sensors with voltage 0~12V
Potential-free outputs NC/NO
Open Collector Outputs OC
Three Outputs for connecting actuators with a maximum of 24VDC
SPDT (Single Pole, Double Throw) relay (toggle switch)
Configurable timer that automatically switches off after a preset period of time (default is 500 ms)
The output can be set to activate automatically when the input terminals
(see configuration setting)
As a Z-Wave Plus certified product, Nexello 3I/3O Hybrid Module supports Z-Wave S2 security. The following security modes are directly supported:
- S2 Authenticated
- S2 Unauthenticated
ABUS describes Nexello 3I/3O Hybrid Module as having the following features:
- Battery Quantity
- Battery powered using AAA batteries
- FLiRS capable
- Supports Network Wide Inclusion
- Supports Z-Wave Explorer Frames
- Supports Z-Wave SmartStart allowing you to setup the product simply by scanning its QR code via
SmartStart QR code's location as follows: The DSK code (Device-Specific-Key) is the device-specific key of your device and is required for secure teach-in (inclusion) via S2 on the Z-Wave controller. The first 5 digits of the DSK Code can be found under the QR Code on the back of the product.
Press the Link button 3 times quickly (within 1.5 seconds) to start the inclusion on the device. The LED starts flashing green quickly.
Press the Link button 3 times quickly (within 1.5 seconds) to start the exclusion on the device.
The device is an Always On Slave and therefore does not require a WakeUp function. The device can be controlled by the Z-Wave controller at any time.
Factory reset Nexello 3I/3O Hybrid Module
Press the Link button 3 times quickly (within 1.5 seconds).
Press quickly (within 1 second)
a fourth time and press and hold the Link button for at least 5 seconds.
The device is now reset to factory settings.
This procedure should only be used if the primary network controller is not capable of acting.
If the device is set to factory default, the status is set to "not included" and the association settings and possible configurations are reset to default.
Please note that this is a user manual Nexello 3I/3O Hybrid Module from ABUS is provided as is and without warranty; all information contained herein is provided by the manufacturer or the certifying body. The information provided is for reference only and is not intended to be used as a substitute for professional advice. ZWaveProducts.com only warrants and is only able to support products purchased directly from us. If you have Nexello 3I/3O Hybrid Module and have not purchased it from us, please contact the manufacturer directly with any further questions you may have.